Dalian caseberg equipment manufacturing co. LTD
Marketing center: dalian Shahekou District changxing street 137-139 fuhung international tower B 2301
Mail box: email@example.com
Negotiation hotline: +86-0411-62278511
Contact number: +86-18018919688
Company website: WWW dlcosbog.com
Kesberg fluid technology (qingdao) co.LTD
Marketing center:137 Yanqing Road, Huanxiu office, Jimo District, Qingdao
Compressed air pipe, pipe selection: compressed air pipe commonly used for seamless steel pipe. Valve, pressure reducing device, oil and water discharge device, compensator, valve and meter are installed in the pipeline system. All of them are selected and processed according to the design drawing. It's made of stainless steel. It's fine, but it's expensive. 2, with galvanized pipe, will rust, cheap price. 3, with PPR, the price is cheap, but a long time to break, not safe. 4, new aluminum alloy pipeline, not rust, corrosion resistance, zero leakage, expensive, fast installation. The soft-wall air compression tube has the appearance, softness, elasticity similar to rubber, oxidation resistance, anti-aging, not soft in summer, not hard in winter, not cracking characteristics.
Need to disinfect, compressed air pipe can breed bacterium, must disinfect regularly. My factory is to use ozone disinfection compressed air pipeline, we buy is the indoor ozone occurred. Sterilizing method: connect the ozone outlet to the pipe with a soft connection, ozone concentration is 10ppm, sterilize for 30 minutes each time, and sterilize once a quarter.
If there is water or other dirty things in the compressor pipe is blocked, after blocking to clean and replace refrigerants and filters, which is a very complex work, to be repaired by professional maintenance personnel. Gas, liquefied gas, steam medium or flammable, explosive, corrosive, toxic, corrosive liquid medium with high operating pressure greater than or equal to 0. IMPa, nominal diameter greater than 25mm. When the product is installed in the main pipeline of the air compressor station, it should be at least 10 meters above the outlet of the air compressor. The lower the temperature of the pipeline, the more suitable for installation.
Compressed air pressure reducing valve by the main valve and guide valve two parts. The main valve mainly consists of valve seat, main valve disc, piston, spring and other parts. Guide valve is mainly composed of seat, disc, diaphragm, spring, regulating spring and other parts. The outlet pressure is set by adjusting the spring pressure, and the diaphragm sensor is used to change the outlet pressure. The piston is driven by the opening and closing of the guide valve to adjust the over-flow area of the throttle part of the main valve, so as to realize the function of reducing pressure and stabilizing pressure. At present, many users are still using carbon steel pipe and galvanized pipe; Carbon steel pipe used for a long time inside the pipe will naturally have corrosion impurities deposition, corrosion penetration leakage pipe.
The compressed air pipeline in hot regions should be laid overhead and thermal compensation should be considered. When the compressed air pipeline is laid overhead in cold area, anti-freezing measures should be taken. The connection of compressed air pipeline, choose welding, can ensure the leakage in the transmission process is small.